Thông tin chi tiết
Cây thử đầu báo khói TSE-A100
1. Remove the TSE-A100 from its carrying case.
2. Unscrew the combustion chamber from the bottom of the TSE-A100.
3. Unscrew the punk stick holder retainer from the combustion chamber.
4. Insert a punk stick into the punk stick holder in the combustion chamber.
5. Light the punk stick with a flame.
6. Reassemble the combustion chamber.
7. Screw the combustion chamber back into the bottom of the TSE-A100
8. Extend the telescopic pole of the TSE-A100 to a length which enables you to reach the detector you wish to test.
• Tests all types of smoke detectors.
• Completely self contained and portable.
• Extends from 5.25 feet to 14.1 feet.
• Internal Smoke Source.
• Non-Toxic Smoke Source.
• Unit includes shoulder sling carrying case.
• Optional adapter for high velocity conditions.
• Exhaust function to clear detector.
• Built-in filter to prevent tar residue from adhering to the surface of the detector.
Khi có nhu cầu các bạn hãy nhanh tay liên hệ với chúng tôi
CÔNG TY CỔ PHẦN TM-XD PCCC QUỐC AN
Đ/c: 212 Cộng Hòa – P.12 – Q.Tân Bình – TP.HCM
Tel : (028) 2247.1234 – 22.411.113